We have performed the ASHRAE test on these hoods and they all passed. The alarms do go off frequently and so are ignored. So I am concerned about the wolf and have stated as much in writing. I have been asking for the monitors to be serviced. Starting with the monitors and followed with your suggestions may be enough to move through the block.
On Mon, Apr 29, 2013 at 4:57 PM, Yung Morgan <pmorgan**At_Symbol_Here**ehs.umass.edu> wrote:
For the new high efficiency hoods, require an Ashrae 110 test as manufactured(AM) and another one as installed (AI) for at least 10 or 20% of the hoods in your facility.
Air flow alarm visible( with numbers) and audible are a requirement. When testing the hoods we have a required that the hoods pass at flow rate: 80 FPM(70-90FPM) at 18 inches opening and hood alarm set at 55FPM , sash response time at 60 sec or less. Ask for a balancing report also to be sure the supply is proper for the space as a VAV hood will not work without enough supplied air, hence the constant flow alarm which can be a nuisance to the occupants. Fume hoods sensors are not always useful as research hoods have to run overnight at optimum flow rates, a constant battle between the energy group and safety people. Room occupancy sensors are fine as long as the researchers know to not to work in the dark(with the light off) unless they want their hoods air flow to go down.
Again, just my two cents.
Yung Morgan, MsPH
Industrial Hygiene Services
Environmental Health and Safety
117 Draper hall
UMASS,Amherst MA 01003
phone (413) 545-2682
Fax (413) 545-2600
email : pmorgan**At_Symbol_Here**ehs.umass.edu
I would like to start a discussion on current experience with chemistry fume hoods related to overall quality, best value, interior construction, coatings/materials of construction, installation issues, air flow alarms, order lead time, energy saving features plus anything else that comes to mind.
James S. Johnson Ph.D., CIH, QEP
JSJ and Associates
Pleasanton, CA 94588--
Mary Ellen Scott, PhD.
Safety Specialist II
Case Western Reserve University
EHS - Environmental Health and Safety
Service Building 1st Floor Rm 113
2220 Circle Dr.
Cleveland, OH 44106-7227
"There is no science without fancy and no art without fact" =96 Vladimir Nabokov (1899-1977)
Previous post | Top of Page | Next post