On our campus we vent cabinets to the fume hood exhaust system whenever practical to cut down on the exposure when opening them
Russell Vernon, Ph.D.
Environmental Health & Safety
University of California Riverside
900 University Ave
Riverside, CA 92521
Trip Location Intellegence for Planning:
https://ermsp.ucop.edu/uctrip and enter your UCnet ID
From: DCHAS-L Discussion List [dchas-l**At_Symbol_Here**MED.CORNELL.EDU] on behalf of Debbie M. Decker [dmdecker**At_Symbol_Here**UCDAVIS.EDU]
Sent: Thursday, December 05, 2013 3:40 PM
Subject: Re: [DCHAS-L] Flammable cabinet storage best practices
Go here and access our guidance on vented flammable liquid storage cabinets: http://safetyservices.ucdavis.edu/ps/fp/fn/biefs/ventingFlammableStorageCabinets.pdf/view
Also, in the context of Fire Code compliance audits, our designated campus fire marshal offers this guidance:
"According to NFPA 30, Flammable and Combustible Liquids Code Handbook, venting a flammable storage cabinet is not necessary for fire protection purposes.
Flammable and combustible liquid storage cabinets are designed to protect the internal contents from a fire outside the cabinet. An improperly vented cabinet could compromise the ability of the cabinet to protect its contents from a fire.
According to NFPA 30, 6.3.4, "The cabinet is not required to be vented for fire protection purposes. However, the following shall apply:
(a) If vented for whatever reasons, the cabinet shall be vented outdoors or to the fume hood exhaust duct in such a manner that will not compromise the specific performance of the cabinet.
(b) If the cabinet is not vented, the vent openings shall be sealed with the bungs supplied or with bungs specified by the manufacturer."
If vapor or odor is an issue there is a product called VAP-R GARD. That can be attached to the inside of the cabinet I have attached the link.
Hope this helps -
Debbie M. Decker, CCHO
Department of Chemistry
University of California, Davis
1 Shields Ave.
Davis, CA 95616
Birkett's hypothesis: "Any chemical reaction
that proceeds smoothly under normal conditions,
can proceed violently in the presence of an idiot."
From: DCHAS-L Discussion List [mailto:dchas-l**At_Symbol_Here**MED.CORNELL.EDU] On Behalf Of Ralph B. Stuart
Sent: Thursday, December 05, 2013 12:22 PM
Subject: [DCHAS-L] Flammable cabinet storage best practices
A discussion today about proper venting of flammable storage cabinets led to the question of what is the best approach to managing chemical storage in the cabinet to control accumulating fugitive odors. I wonder if anyone has written guidance for a Chemistry Dept audience for that addresses this question?
Thanks for any help with this.
Ralph Stuart CIH
Chemical Hygiene Officer
Department of Environmental Health and Safety Cornell University
Previous post | Top of Page | Next post