> These velocities exceed 200 f/m in some cases.
I found many of our hoods were over 140 fpm; the good news is that the labor costs associated with getting them recommissioned to the design velocity (80 fpm) is easily paid for by the energy savings previously mentioned (and then some).
Ralph Stuart, CIH, CCHO
Chemical Hygiene Officer
Keene State College
Previous post | Top of Page | Next post