I send this question regarding a recent internal audit of our cGMP facility. There is a recently constructed hallway which runs 70' and does a 90-degree "L-turn" to a 15' hallway.
We currently have one extinguisher at the end of the 70' hallway. I feel that a second extinguisher should be placed atthe end of the 15' section as well.
Can anyone provide guidance, or an NFPA reference?
Thank you in advance.
George D. McCallion
QA Reviewer, Quality and Compliance
QS Pharma, LLC
3 Chelsea Parkway, Suite 305
Boothwyn, PA 19061
Office: 610.485.4270, ext. 245
Previous post | Top of Page | Next post