From: ILPI Support <info**At_Symbol_Here**ilpi.com>
Subject: Re: [DCHAS-L] Magnesium/Dry Ice Demonstration - fire extinguisher?
Date: Sat, 13 Aug 2016 10:31:52 -0400
Reply-To: DCHAS-L <DCHAS-L**At_Symbol_Here**MED.CORNELL.EDU>
Section 22.214.171.124 is titled "Applications of Extinguishing Agents". Section 126.96.36.199.1 specifically mentions dry sand, other dry compatible material, or Class D powders as extinguishing agents. So that settles the dry sand question for good.
The standard also has a chapter on magnesium and Annexes on supplementary info as well as explosibility of Mg.
Section 188.8.131.52 lists many points about planning for such fires, including a statement at point (5) that dry chemical extinguishers on non-alkali metal fires are ineffective at controlling the metal fire, but can be useful when other materials are on fire and the metal is not yet on fire. Wow, this whole section has some really amazing facts about flammable metal fires; I knew a lot of this but I keep finding more neat tidbits as I read it - I encourage everyone who works in this area to give this document a good read!
At only $59.50 for a PDF of print copy, I'd say any organization working with flammable metals would want to purchase this one if they don't have it already.
Safety Emporium - Lab & Safety Supplies featuring brand names
Fax: (856) 553-6154, PO Box 1003, Blackwood, NJ 08012
I have quite a bit of experience remediating alkali & reactive metals, and as Steven stated for what you are proposing to demonstrate, i.e. the small quantities - there is a simpler solution to not "lugging" around a heavy Class D Powder
- fire extinguisher. Class ABC, or Class BC Dry Chemical
fire extinguishers use "dry chemicals" and Class D "extinguishers" use Dry Powders
. Yes, there is a distinction between the two.
Previous post | Top of Page | Next post